GL-75-3SP-MZP3, Scheduled Release Greywater Processor, 75 Gallon, 3 Stage Pump, 115V 830WFlotender
Made In The USA
The maximum GreyWater source in one hour will be:
- 3 showers or
- 2 showers and 1 load of laundry or
- 1 bath
Drip Zone Sizing for a level yard
The maximum zone size can be 360 Gallons/Hour
Netafim BIOL 560 045 0.60GPH 12.00IN 500FT, 100FT
Purple Wastewater Drip Pipe, .6 GPH, 12" Spacing
Drip Zone Sizing for a yard with 10 ft elevation rise
The maximum zone size can be 220 Gallons/Hour
1 - 75 Gallon Greywater Processor
1 - Expansion Reservoir Connection Assembly
1 - Scheduled Release Controller
1 - Pump Relay
4 - Drip Irrigation Electric Zone Valves
1 - 3" Intake Diverter Valve
1 - Secondary Filter Assembly including Performance Indicators,
Filter Wash Strainer, Filter Wash Regulator and Connection Tube.
- Drip Tubing
- Greywater Intake Pipe from the house
- Greywater Overflow Pipe
The first step in the Flotender system installation is to determine the location of the greywater processor. In flowing greywater must be either gravity-fed from the building's greywater stub-out or pumped into the greywater processor using an external transfer station. (sold seperately)
Above-ground Greywater Processor Installations
Place the greywater processor at an elevation which can be gravity-fed from the stub-out from the building. It is recomended that the processor and external components are placed on a level surface with at least 29" of clearance above the top of the processor's lid for filter removal.
In-Ground Greywater Processor Installations
For in-ground installations, excavate and place the greywater processor on 1 inch of compact sand. Sand will protect the bottom of the processor from sharp objects and help in leveling. Refer to the following diagrams when placing the greywater processor. Ensure that the incoming greywater is able to gravity-flow from the building stub-out.
Low Greywater Stub-Outs
For installations where the greywater stub-out is below the intake of the greywater processor, a lift station may be installed. The lift station features a built-in pump, and activation float switch which pumps the incoming greywater up and into the processor intake port.
Shown below are three possible overflow configurations to accommodate overflow during periods of lint flushing or large greywater inflows.
AFS-GL Optional Auto-Fill
An upper and lower float switch adds water at a low water level and turns it off when water reaches the upper float.
Level Activation Controller, Auto-Fill Controller, Sensor w/ Mounting Bracket, Auto-Fill Valve, 20 ft Auto-Fill Cable, 20 ft. 24V Power Cable.
GL Series Air-Gap Assembly shown Above.
Includes Air-Gap Backflow Preventer, Pipe and Fittings
The Flotender GL-75-3SP-MZP3 gray water system is a way of reusing water from your household activities, such as washing clothes, dishes, or bathing, to irrigate your landscape. This can help you save water, money, and benefit your plants.
The Flotender gray water system filters the water so it can be distributed by the Netafim Bioline 560 dripline tubing that is manufactured specifically for wastewater applications. It is the world’s most advanced continuous self-cleaning, pressure-compensating dripline for gray water. The Flotender gray water system delivers filtered and pressurized gray water to the Netafim Bioline® dripline into the soil with great precision, ensuring that the gray water does not flood an area or become exposed to people or animals. By distributing the gray water into the ‘biologically active soil horizon’, it not only allows the soil to break down the grey water, but it also allows plants, trees, bushes, and grass to use it, along with its nitrogen and phosphorus content – two of the three ingredients in fertilizer. This ecologically sound process helps protect against the contamination of lakes, rivers, streams and drinking water sources, and it provides an important benefit – the gray water is no longer “wastewater." Flotender turns gray water into reusable, renewable, and beneficial water that becomes a supplement to or replacement for an irrigation system. The best way to recycle gray water from your home, apartment building, or commercial building.
The Flotender gray water system can use water from any source, except the toilet or kitchen sink. The Flotender gray water processor tank usually connects to a gray water stub out that is a plumbing pipe installed during the construction of the house or building and is intended to be used for a gray water irrigation system. It is capped at the end and is usually located outside the house or building. To use it, you connect the pipes from the exterior section of the stub-out pipe to the Flotender gray water system and thereby distribute the gray water into the landscape through the Flotender gray water recycling